Belarus NPP is the 1st nuclear power facility of the latest III+ generation, built abroad using the Russian technologies
Ostrovets (Belarus), October 6 - Neftegaz.RU.
Hot functional test
of the reactor plant, a large-scale stage of commissioning works before the physical start-up, has been completed successfully at Unit 2 of Belarus NPP
(its General Designer and the General Contractor being Rosatom).
In the process of hot functional test, the specialists conducted over 260 various tests, the main purpose of which is to confirm compliance of nuclear island systems and equipment with design characteristics, including safety check of power unit operation at the nominal parameters and during heat-up and cool-down of the reactor
At the nominal parameters stage (at primary circuit pressure 160 kg/sq.cm and temperature +2,800С), operability check of all 4 reactor coolant pumps, main steam pipelines blowdown with auxiliary steam, operability check of reactor plant control and protection systems and auxiliary power
systems were carried out.
Besides, tests of steam generator
main safety valves, pressurizer and many other operations were performed.
Vitaly Polyanin, Vice President - Director of Belarus NPP Construction Project of ASE, said:
- The tests conducted have proven that all the equipment and power unit process systems, involved in the hot functional test program, meet the design characteristics
In accordance with the plan of power unit preparation for physical start - up, the next stage is inspection of the main and auxiliary equipment of the primary and secondary circuits of the power unit
The Russian design of III+ generation was chosen for the 1st
NPP in Belarus
, which fully complies with international safety
standards and recommendations of the IAEA